|UFDC Home||myUFDC Home | Help ||
ALL VOLUMES CITATION THUMBNAILS PAGE IMAGE ZOOMABLE
STANDARD VIEW MARC VIEW
PROJECT: Restoration of DeMesa-Sanchez House
St. George Street
St. Augustine, Florida
State Project No. DOS-3200
OWNER: Historic St. Augustine Preservation Board
ARCHITECT: Shepard Associates, Architects & Planners, Inc.
DATE: July 19, 1979
ADDENDUM NO. 1
The Contract Documents dated 5 February 1979 or as revised 20 April 1979
for the project noted above are hereby amended as indicated in this Adden-
dum No. 1. This addendum shall become a part of the Contract Documents.
CHANGE THE PROJECT MANUAL AS FOLLOWS:
ITEM NO. 1
Below Alternate No. 1, add spaces for Alternate No. 2 and Alternate No. 3.
CHANGE THE SPECIFICATIONS AS FOLLOWS:
ITEM NO. 2
SECTION 1A BASE BID AND ALTERNATES
Paragraph 1A-3 Alternates:
"Alternate No. 2: Revise Panel P to 150 Amp main breaker and reduce ser-
vice entrance to 1" C. with 3 #1/0.
Alternate No. 3: Mechanical Contractor shall connect 1" piping to valved
connection at well head. Well and valved connection shall be by Owner."
ITEM NO. 3
SECTION 15A HEATING, VENTILATION AND AIR CONDITIONING
"15A-3I(8) Option: The Contractor may elect to use concrete encased round
sheetmetal ducts below the first floor slab and round sheetmetal or fiber-
glass above the first floor slab. All ductwork construction and installa-
tion shall be in accordance with S.M.A.C.N.A."
ADDENDUM NO. 1 (Continued)
CHANGE THE DRAWINGS AS FOLLOWS:
ITEM NO. 4:
SHEET NO. M-2/SECOND FLOOR MECHANICAL PLAN
AtControls Note No. 1, change last sentence to read as follows:
"Space temperature shall be controlled by standard room-type thermostats
located as directed by the Owner."
(END OF ADDENDUM NO. 1)